Please note: If your service address in Central London we will charge a Service charge from £25 (depend on location).
Here is what we will do...
Locating the most appropriate place for the cylinder. Convenient location
Secondary return connection is required to connected and piped to the system or capped off.
Connect the cold wazer inlet, hot water outlet and primary flow and return pipework to the cylinder.
The expansion vessel attached to the wall-mounting bracket and positioned. connected to the cold water inlet group.
Fit the dual thermostat on the sensor/thermostat pocket on the cylinder.Comply G3 regulation.
Fit two-port zone valve operated by the thermostat group that will be de-energised when the control temperature is reached or in a faut mothe, if the high limit thermostat is activated.The valve zone will close off any further flow of primary water from boiler, de-energising the hot water demand side of the control system.
Installed pipwork for the expansion relief valve, the temperature and pressure-relief valve and the tundish.